It was in the "Ebay finds", which is in the For Sale forum, which has special access rules. Something about spam, I think.Sounds interesting - BUT I get an
to that link - LOL members only?
I have blow out 3 of the PCB's so far, got 26 more to go. PCB releases smoke after 20 seconds. Running 30A at 400VDC, and do not apply load till after the contacts are closed. Plan on running 90A and fails at 30A.
Will Call Manufacturer in morning... Note the different Rev of the PCB.
Hi Linghunt,24 VDC fused at 5A. (3.8A inrush current). Yes, the Black is Common Bus and Red wire is the 24VDC.
Relay works just fine until the load is applied to the to the Contacts.
That is confusing Do you have a diagram or schematic? If you don't want to post it, send it PM (or I will send you my email address). I will keep it confidential.I have a Ground reference to the 24VDC supply at just one point on the common at the 24VDC Supply.
Do pretty good at keeping my Ground bus, Neutral bus, and Common bus seperate. The High Voltage line going through the Relay is (-) with the anode of the HV supply also referenced to the Ground. There is arcing on the HV line at times, but not yet during this phase of testing.